Fire pump adapter assembly installation, should according to the interface, main body, a connecting pipe, check valve, safety valve, vent pipe, control valve order, check valve should be installed and the direction of the use of water from the fire pump adapter into the system; integrated fire pump adapter is installed. According to the installation instructions for its use.
It should be installed on the sidewalk or non motor vehicle running area that is convenient for fire engines. The distance from outdoor hydrant or fire pool should be 15 to 40m.: full number inspection.
Fire pump adapter system should be permanently marked difference between fire pump adapter settings and fire hydrant system, automatic sprinkler, and partition sign. Check the number: full check. Examination method: observation and examination.
Underground fire pump adapter should adopt the "cast iron manhole cover fire pump adapter" logo, permanently fixed sign and set indicates its location in the vicinity of the.
The walls of the fire pump adapter installation shall comply with the design requirements. When the design is not required, the installation height should be 0.7m from the ground, and the net distance from the doors, windows, holes and holes on the wall should not be less than 2.0m, and should not be installed under the glass curtain wall.
This article is provided by the fire hydrant guardrail. Our website is: /, we will provide you with better service with wholehearted enthusiasm. Welcome to your visit.